- General Precautions for All Staff
- Localized Electrical Outage
- Labs & Facilities Management
- Reporting Requirements
- Training Requirements & Assessment
The purpose of this program is to prevent injuries and accidents and to protect University employees from electrical hazards. Work unit specific safety procedures for preventing electric shock, or other injuries resulting from direct/indirect electrical contact, to employees working on or near energized or de- energized parts will be developed and implemented as required.
This program applies to all work operations at UA Little Rock involving electrical systems where employees may be exposed to live parts and/or those parts that have been de-energized. Any work on energized equipment may be done only after it has been determined that this type of work must be performed with the equipment energized. While some lab and Facilities Management employees may work with equipment in the 120 to 600 volt range, most University employees normally work in areas with electrical appliances that operate at 120 volts or less.
Current. Term used to describe electric flow measured in amps/amperage. It is current that can cause electric shock.
De-Energized. Electrical devices that are disconnected from all energy sources including direct electric connections, stored electric energy such as capacitors, and stored non-electrical energy in devices that could reenergize electric circuit parts.
Energized Electrical Work. Work conducted by an employee on or near an exposed energized circuit greater than 50 volts and typically less than or equal to 600.
FM. Factory Mutual –An independent product safety testing and certification company.
GFCI. Ground Fault Circuit Interrupter, which provides additional protection from shocks by shutting off current to equipment when a change in electricity is sensed.
Grounding. Provides a safe path between electricity and the earth, preventing leakage of current; the creation of a conductive path for electricity between a circuit and the equipment to ground.
High Voltage. Electrical systems or equipment operating at or intended to operate at a sustained voltage of more than 600 volts.
Low Voltage. Electrical systems or equipment operating at or intended to operate at a sustained voltage of 600 volts or less.
Polarized Plug. Helps reduce the potential for shock with easily identifiable plugs. One prong is wider than the other and can only be inserted into outlets one way.
Qualified Electrical Worker. A qualified person who by reason of a minimum of two years of electrical training and experience with high voltage circuits and equipment and who has demonstrated by performance familiarity with the work to be performed and the hazards involved. Only a Qualified Electrical Worker is allowed to work on energized conductors or equipment connected to energized high-voltage systems.
Qualified Person. A person, designated by UA Little Rock, who by reason of experience or instruction has demonstrated familiarity with the operation to be performed and the hazards involved. Whether a person is considered to be a “qualified person” will depend upon various circumstances in the workplace. It is possible and, in fact, likely for an individual to be considered “qualified” with regard to certain equipment in the workplace, but “unqualified” as to other equipment. An employee who is undergoing on-the-job training and who, in the course of such training, has demonstrated an ability to perform duties safely at his or her level of training and who is under the direct supervision of a qualified person is considered to be a qualified person for the performance of those duties.
Resistance. The ease with which electricity flows through the material (conductor). Materials (conductors) with higher resistance properties can become hot. (Measured in ohms)
UL. Underwriters Laboratories is an independent product safety testing and certification organization.
Voltage. Electric potential or potential difference assigned to a circuit or system expressed in volts.
UA Little Rock Employees are responsible for:
- Being aware of electrical safety issues
- Complying with safe operating procedures when working with electrical equipment
- Attending appropriate safety training
- Reporting safety concerns
Managers are responsible for:
- Ensuring staff are trained, qualified, and authorized to work on electrical equipment
- Conducting periodic hazard analysis of work areas
- Correcting identified safety hazards
EHS is responsible for:
- Providing assistance in identifying electrical safety issues
- Providing electrical safety training for campus staff
- Reviewing electrical equipment safe operating procedures as necessary
Facilities Management is responsible for:
- Ensuring that all authorized or qualified persons have received appropriate levels of training
- Ensuring appropriate Personal Protective Equipment is provided to authorized or qualified staff who work with electrical equipment
All employees use electric powered equipment and systems throughout the campus. Whether in an office, lab, or workshop, electricity is used continuously, usually without incident. Voltages as low as 12 volts can be dangerous. When working with or around electrical equipment, one may inadvertently become part of an electrical circuit. Only trained and authorized or qualified individuals should do any repair or work on electrical equipment. All staff should abide by the following:
- Never work on “hot” or energized equipment unless it is necessary to conduct equipment troubleshooting.
- Use extension cords only as temporary power sources.
- Do not connect too many pieces of equipment to the same circuit or outlet as the circuit or outlet could become overloaded.
- Be sure that ground-fault circuit interrupters (GFCI) are used in high-risk areas such as wet locations. GFCI’s are designed to shut off electrical power within as little as 1/40 of a second.
- Plug strips, such as those used on computers, should be plugged directly into outlets and not into extension cords or other plug strips.
- Inspect all equipment periodically for defects or damage.
- All cords that are worn, frayed, abraded, corroded, or otherwise damaged must be replaced.
- Grasp the plug to remove it from a socket. Never pull the cord.
- Keep all cords away from heat, oil, and sharp edges.
- Always follow the manufacturer’s instructions for use and maintenance of all electrical tools and appliances.
- Keep equipment operating instructions on file.
- Never touch an electrical appliance and plumbing at the same time.
- Always unplug electrical appliances before attempting any repair or maintenance.
- All electrical devices must be properly grounded with approved three wire plugs unless they are “double insulated”. Grounding provides a safe path for electricity to the ground, preventing leakage of current in circuits or equipment.
- All electrical equipment used on campus should be UL or FM approved.
- Keep cords out of the way of foot traffic so they don’t become tripping hazards or become damaged by traffic.
- Never use electrical equipment in wet areas or run cords across wet floors.
- Ensure energized parts of electrical equipment operating at 50 volts or more are guarded against accidental contact.
- Only properly trained employees should work on electrical equipment.
- Know how to respond to emergencies such as electric shock incidents or fires.
In the event of an electrical outage, please do the following:
- Immediately report electrical outages to Facilities Management by calling 501-916-3390.
- If possible, identify the defective equipment or the cause of the failure, and remove it from service.
- Report this information to Facilities Management personnel upon their arrival.
- Never work with electricity greater than 600 volts without specific permission, training, and written procedures. Notify your supervisor immediately if you have any questions.
- Be able to recognize electrical safety hazards in your work area.
- Ensure that all authorized or qualified persons have received appropriate training in order to operate or repair equipment.
- Keep equipment in good working order to help prevent electrical accidents.
- Maintain a three-foot clearance around electrical panels.
- Electrically operated equipment must be de-energized before work may commence.
- Always follow lockout/tag-out procedures when working on electrical equipment (Lockout/Tag-out Program), and wear appropriate Personal Protective Equipment (PPE) such as safety glasses, rated rubber gloves, rated rubber sleeves, insulated boots, or face shield.
- Never override safety devices such as electrical interlocks.
- Remove all rings, key chains, or other metal objects when working around electricity.
- Wear appropriate personal protective equipment, such as eye protection or insulated gloves, as needed.
- Never use metal ladders when working near energized wiring.
- Damp or wet environments may be dangerous when working with electricity.
- Damp or wet environments may be dangerous when working with electricity.
- Employees working with lasers, performing hardware or software testing, or other activities that do not require direct contact with electrical components, should be aware of electrical safety issues and be alert to the possibility of other employees conducting energized work in the area.
Report malfunctioning equipment or devices to your supervisor or to Facilities Management by calling 501-916-3390. Do not attempt to repair any electrical equipment yourself unless you are properly trained and authorized to do so. Typical issues include the following:
- Damaged cords, plugs, or outlets
- Receiving a shock when touching the equipment
- Arcing, sparking, smoking, or otherwise malfunctioning equipment
Any electrical equipment not operating properly should be:
- Taken out of service immediately
- Tagged or labeled as “Do Not Use”
- Reported to the appropriate department or individual for repair
If safety issues persist, please notify your supervisor.
|Training Requirement||Target Audience||Frequency|
|Basic Electrical Safety Awareness||All UA Little Rock Employees||At time of employment and periodically thereafter as part of the UA Little Rock Safety Training Program|
|Advanced Electrical Safety||UA Little Rock employees who work directly with electrical systems from 50 to 600 volts, Qualified or Authorized Persons||Annually|
|Lock Out/Tag Out||UA Little Rock employees who work directly with electrical systems from 50 to 600 volts, Qualified or Authorized Persons||Annually|
|Hazardous Electrical Voltage Safety||UA Little Rock employees who work with or in the proximity of electrical equipment or systems over 600 volts, Qualified Electrical Worker (QEW)||Annually|
Work unit specific training may also be required for specific workplace activities or equipment. Notify your supervisor if you have any questions. For more information, please contact EHS at 501-916-6351.